API RP 14G: Recommended Practice for Fire Prevention and. 46 Pages · · MB · 93 Downloads ·English. by American Petroleum Institute. Preview. This standard was developed as an API recommended practice under the RP 14G. Fire Prevention and Control on Open Type Ol!~’hore Production Plat- forms. 1 Apr API RP 14G (R). Recommended Practice for Fire Prevention and Control on Fixed Open-type Offshore Production Platforms, Fourth.
|Published (Last):||7 July 2005|
|PDF File Size:||1.20 Mb|
|ePub File Size:||11.10 Mb|
|Price:||Free* [*Free Regsitration Required]|
Unfortunately, there appears to be little formal standardization of the terminology 37 38 API Recommended Practice 14G used to describe fireproofmg systems; therefore, descriptions and meanings may vary slightly from country to country or industry to industry. A water spray system should be designed for a specific design api rp 14g which will achieve one of the above desired effects.
Also, 14h sideration should be given to pr the api rp 14g the api rp 14g temperatures may have on pumps or internal combustion engines. The concentration of a combustible gas can be determined by detection devices that may initiate alarms or shutdowns. The pipe is manufactured under different processes; however, the filament wound process produces the highest strength characteristics in the pipe. CO2 displaces oxygen and will suffocate personnel within a space which it is deployed.
API RP 14G DOWNLOAD
Where a specific class fire extinguisher is recommended below, an extinguisher rated for two or more api rp 14g may be used, provided one rating is the specified class. Fixed stairways or fixed ladders of pr construction. A redline document shows additions, deletions and other content and formatting changes between the active standard and the previous edition.
Such an atmosphere will quickly produce dizziness, unconsciousness, and death if personnel are not removed from the area. After use, hoses and piping should be cleared of residual dry chemical. A Class A extinguisher should be installed in each main corridor api rp 14g quarters buildings. This loss must be taken into account in the design of a system. FM and FE- 1 3 are flurocarbons that have some global warming potential, and can pose health risk to personnel api rp 14g to concentra- 16 API Recommended Practice 14G tions used to extinguish fires.
Where marine growth may restrict water intake, anti -fouling paint or other control measures should api rp 14g considered. The lift column should be encased in a steel pipe for protection against wave action and mechanical damage. Gaseous agents may be used for total flooding of an enclosed area or for local application. Gases such as Carbon Dioxide CO2 and Inergen displace or reduce the concentration of oxygen, smothering the fire. api rp 14g
Copper-Nickel piping has the disadvantages of: Therefore, it is important to use the manufac- turers’ data, which has been established by investigation and tests. Cutting and welding operations should be conducted in accordance with safety procedures established by the operator. Examples of situations where ap may be present on gp platform are the following: The pump must be able to api rp 14g adequate pressure and flow, to the hydraulically most demanding area.
A Class C extinguisher should be installed in radio api rp 14g or other enclosed areas containing a significant concentration of electrical equipment or controls. Electric starters should be approved for the area in which they are installed.
Types of Watermist Systems. In a continuation of this effort, this RP presents guidance for minimizing the pos- sibility of accidental fires and for designing, inspecting, and maintaining the fire control systems api rp 14g open type offshore platforms.
Water can be api rp 14g with other agents such as foam to improve effectiveness in areas with drip pans or solid steel decking.
API RP 14G (R) | MSS Standards Store
The fire control systems discussed in this publication are intended to provide an early response to incipient fires to prevent their aapi.
A one-time extension of up to two years may be added api rp 14g this review cycle. To facilitate the proper use of extinguishers on different types of fires, the National Fire Protection Association NFPA has classified tires as follows: The actual placement of fire extinguishers should be based on a physical survey of the area to be protected.
Consideration api rp 14g be given to using a “butt and wrap” joint design, which is more reliable than the adhesive bonded joint. 41g, the rate of rise required in UL is quite rapid: Combination nozzles are usually recommended to have a psi 6. Quarters buildings should contain products of combustion detectors within each bedroom, corridor, hallway and office.
Extinguishers suitable for api rp 14g B” fires should be identified by a square containing the letter “B. They should be given actual experience in handling the equipment on small practice fires simulating actual situations as closely as possible. They should start reliably and run smoothly at rated speed and load.
Full Description Presents recommendations for minimizing the likelihood of having an accidental fire, and for designing, inspecting, and maintaining fire control systems.